Re: heat stops then blows cold air for several minutes.
There is a board inside the ac, its almost like a motherboard, if it goes bad that will start to happen the arent too cheap to buy but they are easy to fix when you take the wires off of it make sure you put them back on the new one the same way you took them off the oold one
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US. click here to Talk to a Repairman (only for users in the US for now) and get all the help you need. Goodluck!
- If you need clarification, ask it in the comment box above.
- Better answers use proper spelling and grammar.
- Provide details, support with references or personal experience.
Tell us some more! Your answer needs to include more details to help people.You can't post answers that contain an email address.Please enter a valid email address.The email address entered is already associated to an account.Login to postPlease use English characters only.
Tip: The max point reward for answering a question is 15.
Is your 'Heater' you are talking about-- A furnace-- with a burner and a blower?
Either way-- We need to adjust a control that determines WHEN THE FAN RUNS--
Most furnaces have a section where the heated air collects, and there has to be a sensor in that chamber, that senses when that air is warm enough to circulate around--- and when the burner shuts off, the air in that area cools down, and the sensor should shut off the fan-
Can you find the Heated air area?-- and can you find a temperature control in that area?-- Can you adjust the control, so that it shuts off the fan when the air temp drops to 100- to 120 degrees F...
Tell us more about the type of furnace/heater we are workig with, so I can better help you-
Check wiring done correctly. Symbolsin remote:
To get proper cold air set temp 23 degree and mode"cool". To get heat set temp 30 degree and mode in "Heat"
Now symbols: 1. fan leaves - Fan only 2. Rain drop- Dry mode 3. Snow flake-Cool mode 4. Sun- Heat 5. A or AU- Auto mode.
Find a reputable HVAC contractor to do a
room by room analysis with heat and cooling loads calculated and units
sized and duct requirements and compare to what you have.
The air not being cold is not necessarily an indicator of anything
malfunctioning. High efficiency units for instance don't produce cold
Since you have had someone look at it, the duct
work may be collapsed which restricts air flow or uninsulated which
warms up the supply air. Either one is a possibility. Any Cox Cable guys
been stompin' around your attic lately? Wouldn't be the first time.
Usually, when the air coming out of the vents is not cold enuf it's because your freon level is low. Probably leaking, but they can usually recharge the freon and it will work for a while. Try another repair company and see if they can recheck the freon level.
We have a high efficiency unit and it produces cold air, so I don't know what previous poster is referring to. Air conditioners are supposed to blow cold air.
Sorry, to tell ya but it is normal if the outdoor temperatures are much
below 45 degrees. Below 45 degrees there is little heat outdoors for the
heat pump to grab to heat the home so it will run 24/7 and blow cool or
cold air. Below 45 the temp of the air coming out the vent will decline
and you will get no heat from the heat pump itself as you near
Your emergency heat or auxiliary heat is electric strip heat. But it
only kicks in during normal operation if the temp in the house drops 3
degrees below the setting. (some tstats if can be 5 deg.) Otherwise the
heat pump will blow cool or cold air the rest of the time if it is too
To prevent it from running all the time and blowing cold it is
recommended if the temp outside is falling below 45 degrees you should
just switch to the emergency heat setting, which shuts the pump outdoors
off, and just heat with the electric.
But if there is no heat outside the heat pumps will blow cold. They are
the cheapest and most efficient forms of heat but only as long as the
outdoor temp is above that 45 deg..
I'm guessing that if you haven't experienced this you live in some place
with moderate winter temperatures like in Northern Florida and rarely
get very cold winter temps like the freezing you have seen there
It will likely blow much warmer when the outdoor temp rises.
See if you can reposition the thermister on the facing of the evaporator coils. That could be it or the thermister might be bad. They don't use copper/mercury sensing bulbs these days. They use these cheap thermisters.
plus one on the cooling fan problem. if it was low on charge then as you slow down, condensor temps and line prressures would raise therefore it would cool at low speed and and not when moving since the incoming air would drop system temp,reducing line pressure and then cusing compressor to cycle. the auxillary cooling fans must be on whenever a/c is on, if not, thats your problem. get this taken care of because if you get stuck in traffic, your engine will overheat also if fans are not running