Question about Fahrenheat LFP6152 Halogen Baseboard Heater
I recently changed the 100 amp breaker for the furnace because it what making a lot of noise and was very hot, and it made the main breaker 200 amp went off one morning last week. I changed the 100 amp breaker yesterday, put the furnace on and this morning the upper part of the main box was hot and ther was a smell coming fromm the box. I put the furnace back on oil, but during the day the lights were blinking a bit and the panel is still hot. Should i replace the main breaker 200 amp.
This is a dangerous situation! There is a short in the furnace. It is NOT a breaker problem! You need to check the current draw in the furnace circuit, This requires an Amprobe meter. If you don't have one, contact a technician at once! You have a fire hazard!
Posted on Dec 15, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 17, 2015 | Electrical Supplies
May 31, 2014 | Cutler Hammer 100 Amp Main Breaker...
Jan 06, 2014 | Electrical Supplies
Nov 04, 2012 | Bryant Westinghouse Bqc Quad Circuit...
Oct 06, 2012 | Bryant /murray Bj2200 Main Circuit Breaker...
Jan 16, 2012 | Your One Source 100 Amp Main Lug Load...
Jun 13, 2011 | Siemens 100 Amp Main Breaker Renovation...
Dec 20, 2010 | Siemens 200 Amp Main Breaker 30 Spaces 40...
Jul 14, 2009 | Siemens /ITE 100Amp 2-pole molded circuit...
Dec 17, 2008 | Prime 10 Amp Circuit Breaker
257 people viewed this question
Usually answered in minutes!