Question about Goodman GMS90703BXA Heater
Unit is actually an Amana 90. It looks just like the Goodman Furnace.
Condensation is leaking out of the bottom of the black plastic cover where the ventor motor is mounted. Are the cover bolts loose?
It is just a slight trickle of water, but it collects and causes rusting of the metal panels.
Is there a “proper’ fix for this? Is the furnace not level?
Probably a bad gasket between the inducer housing and the secondary heat exchanger. They may be available from a goodman dealer.
Posted on Jan 04, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 13, 2016 | Dayton Heating & Cooling
Nov 16, 2014 | Goodman Heating & Cooling
Jan 28, 2014 | Goodman Manufacturing Goodman 60,000 btu...
Feb 24, 2011 | Heating & Cooling
Feb 03, 2010 | Goodman Heating & Cooling
Jan 04, 2010 | Heating & Cooling
Dec 13, 2009 | Amana PTC074B25AE Electric Heat Air...
Oct 13, 2009 | Goodman GMS90703BXA Heater
Feb 11, 2008 | Goodman GMS90703BXA Heater
If the exhaust comes off the top of the furnace, you will need to make sure the condensation will drain all the way back to the condensate outlet found at the base of the inducer blower. If you are having to remove the tube from the pressure switch, there must be a blockage from the inducer down to where ever it drains to. Check to see if all tubes are free of blockages and if there is a condensate trap, clean it out. If the pressure tube you mentioned is facing up toward the blower allowing water to flow into it, reposition it so water will not enter the tube.
Oct 17, 2007 | Ruud UAKA030 Air Conditioner
686 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: