Question about Hitachi RAS-09UH Air Conditioner
Its 22 F outside I have a outdoor Infinity that will not run .The indoor is fine Its a fish store with lotsa great stuff but need cooling 'Its a 4 ton unit its been fine when temps are 28 to 32 help or I'll be eating lots
Running an air conditioner in the winter.
Generally they have a low pressure switch on them that won't allow it to run when the pressure falls below about 60 psig, at 22° F refrigerant R22 pressure is about 45 psig.
So to run it at that temperature you will have to disconnect your low pressure switch and install a jumper wire across those terminals and install a low ambient fan cycling switch kit (that you can get at your local ac parts house) which will keep the head pressure up when unit is running.
But by bypassing the low pressure switch you won't have any protection if you have a refrigerant leak or your indoor blower fails
or filter or evaporator gets dirty or plugged up.
Posted on Apr 10, 2009
Some air conditioners have a thermostat that will not allow the compressor to run below a certain out side tempature as it will cause liquit to come back into the compressor(called slugging) and damage or destroy it.
Posted on Jan 08, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 28, 2017 | Heating & Cooling
Dec 31, 2013 | Heating & Cooling
Jun 11, 2017 | Heating & Cooling
Aug 26, 2011 | Carrier 38CKC036 Air Conditioner
Double check the batteries to make sure they are installed correctly. If one of the batteries in the outdoor sending unit is in backwards, it will not send the outdoor data. On the indoor unit, there is typically one battery that is used for receiving the signal from the outdoor unit. If all of the batteries are in correctly but that one, you will see the display and the indoor temperature information, but the outdoor information will not be displayed.
Aug 27, 2010 | Acu-Rite Adagio Clock Radio
Apr 18, 2010 | Ruud UBHC Air Conditioner
Sep 30, 2009 | GE Quiet-Aire Ductless Split System Air...
Apr 15, 2009 | Fujitsu 18R1 Air Conditioner
Apr 26, 2008 | Heating & Cooling
May 04, 2014 | Hitachi RAS-09UH Air Conditioner
219 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: