Question about Water Heaters
C.H o.k but no hot water but boiler fires when tap opened
If the boiler fires when the tap is opened then the diverter valve is working ok it must be a blocked plate heat exchanger which is the stainless steel rectangular block inside the boiler connected to the pump and the mains cold water.
it will be blocked on the central heating part probably with black scale. it is possible to clean out but sometimes it is better to just change the plate. but remember to flush the system as well or the same thing will happen.
Posted on Mar 30, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 09, 2016 | Water Water Heaters
Jan 24, 2015 | Water Water Heaters
Jan 19, 2013 | Water Heaters
Dec 20, 2012 | Water Heaters
Sep 15, 2017 | Bosch Water Heaters
Mar 28, 2009 | Water Heaters
Mar 23, 2009 | Water Heaters
Oct 23, 2008 | Water Heaters
Oct 15, 2008 | Protech Systems FasNSeal FSWMKE4 4" Vent...
273 people viewed this question
Usually answered in minutes!