Question about Hayward H Series Pool & Spa Heater 400k Btu Propane Gas Milivolt Ignition H400p1
I have not used the heater for over 6 months. The mode lights work correctly. It is on Standby as it should be. I selected SPA and set the temp for higher. The mode light flashed green but the heater did not light. Then a fault code of 1 F appeared. The same sequence of events occurred in the Pool mode. Should I have the tank filled and the system bled before I call for maintenance? Or do you have any other suggestions? Thanks, Phil Ragan
IF stands for ignition failure, one possible cause is that the two sparker prongs are not spaced properly, i have seen this before several times. The correct distance for them to be spaced apart is the width of two quarters side by side... not like this....OO, the other way so the are flat. To access that you have to take out the heat exchanger, which requires unhooking high limit switches in the back, unhooking the pressure switch, thermostat wire, and plumbing...just remember where everything goes. Before you do that though check this simple thing...there are a number of brass orifices that shout gas to the burners, use a 7/16 wrench to take off the one that is to the extreme left, which is on the igniter side of the heater, inspect the orifice to see if there is blockage, like a spider web or something. If it is blocked, clean it out and also look down the burner itself to see if it is free of blockage. And because we all make simple mistakes.......make sure the gas is on.
Posted on Jan 08, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 26, 2012 | Hayward H-series Electronic Gas Pool...
May 13, 2012 | Hayward H Series Pool & Spa Heater 400k...
May 07, 2012 | Hayward H-series Electronic Gas Pool...
Dec 30, 2009 | Hayward H Series Pool & Spa Heater 400k...
May 26, 2009 | Hayward H - Series 400 Heater Top for In -...
367 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: