Question about Ruud Heating & Cooling
I have a Ruud AC/Furnce that was here when I moved in, so I do not know the model. The problem I'm having is that when the hearter turns on, the gas ignites, but doesn't stay lit, and making it so that the heater never fully turns on. The a/c side and fans work.
Any help you can givre is appreciated.
Sounds like it may be a bad flame sensor. After the ignition, the flame sensor needs to send 24v back to the gas valve to indicate the the ignition took place. If it does not do this, the gas will shut of as a safety precaution. The flame sensor can often be cleaned up with a piece of sandcloth to fix this problem, or it may be replaced.
Posted on Dec 16, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 29, 2012 | Ruud Heating & Cooling
Aug 08, 2011 | Ruud UBHC Air Conditioner
Mar 31, 2010 | Ruud UBHC Air Conditioner
Mar 29, 2010 | Heating & Cooling
Oct 18, 2009 | Heating & Cooling
Oct 17, 2009 | Heating & Cooling
Feb 11, 2009 | Ruud Central System Air Conditioner
114 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: