Question about Heating & Cooling
My storage heater is from the iron age. it had 2 dials. one says room temp 1-6 and the other says auto set control 1-6.
what do i need to set it as to get heat???
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Storage Heater
You will need a volt/ohm meter. remove the element or at least the wires on each end. set the meter to ohms, touch each lead from the meter to the opposing ends of the element. The meter should have some type of resistance. If it shows open or the needle doesn't move (on the older non digital type) then the element is bad.
Posted on Jan 05, 2008
Suspect a fuse blown. These are normally easily accessible at the top of the heater, once you have ISOLATED the supply and removed the cover, very carefully. (MAY be asbestos inside, if they are old heaters...)
Posted on Aug 18, 2008
The dial on the wall with 1-24 on it, with the red pins, is the timeswitch to turn the heater on for night-rate hours (when the electricity is cheapest). Hour 1 is 1am --> Hour 24 is midnight.
Set the red pins to turn the heater on from 11PM (23) to 7am (7). The 'on' symbol is normally a '1', with off being '0'. Otherwise, on can be symbolised with a staright line with circles on it, while off is like a little barrier-arm part up.
As for the knobs on the heater, one is for the amount of heat which goes in (how much the heater 'charges'), and the other is for how much it lets out.
Genrally in winter you set the input (nite-store, second knob) to full (6), but in spring or autumn you may reduce this as required.
The other knob (room temp) is for how much heat comes out of ther heater. If you work during the day, you will want to conserver the stored heat in the heater.
Turn the room temp knob down to about 3 when you leave for work, and wind back up to 6 when you get home. This will stop all the heat leaving the heater during the day (and maybe use less power to recharge at night).
Good luck with the time switch. Check your night-rate hours on your power account.
Posted on Jun 21, 2009
Tips for a great answer:
Nov 27, 2017 | Heating & Cooling
Nov 24, 2014 | Heating & Cooling
Sep 20, 2011 | Heating & Cooling
Feb 02, 2011 | Comfort Zone CZ9009 Oil Filled Electric...
Dec 02, 2009 | Fahrenheat FBE15002 Baseboard Heater
Oct 27, 2009 | Dimplex DS5603 Heater
Apr 03, 2009 | Heating & Cooling
Oct 05, 2008 | Procom ML300HGA Heater
Jan 03, 2008 | Heating & Cooling
301 people viewed this question
Usually answered in minutes!