The pilot light will stay lit, but the burner no longer comes on. I typically heard a click when the valve opens, but I'm not getting that anymore. I suspect the thermocouple, but wanted to know if there were any other items to check out, and any way to verify that the thermocouple is bad before I schlep off to find one.
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US. click here to Talk to a Repairman (only for users in the US for now) and get all the help you need. Goodluck!
- If you need clarification, ask it in the comment box above.
- Better answers use proper spelling and grammar.
- Provide details, support with references or personal experience.
Tell us some more! Your answer needs to include more details to help people.You can't post answers that contain an email address.Please enter a valid email address.The email address entered is already associated to an account.Login to postPlease use English characters only.
Tip: The max point reward for answering a question is 15.
I would first check the gas pressure to your furnace. Then make sure that burners are clean and watch flames when burner first ignites. I have seen burners that were dirty cause delayed ignition that would create a suction when they came on and extingush pilot and burners.
The next thing I would do is change gas valve. Thank you
Remove front cover,or just lower section if you can. they usually just need to be lifted up about an inch or so and pulled out. However some have covers that snap in place. After you remove cover locate gas valve. It should have a control knob on top with markings for on, off, and pilot. Set control to pilot. Follow lines from gas valve to burner compartment, one goes to main burner one ,small copper colored line is the thermocouple, other line is the pilot. Turn thermostat down as far as it will go. Make sure gas supply valve in line to heater is on and then depress pilot control , when you have pilot control depressed have a match or other small flame source close to pilot assembly. If it lights then hold down on pilot control for a couple of mins. Slowly release pilot control and if it stays lit turn gas control to on. Turn thermostat up to call for heat and burner should light. If pilot doesn't stay lit when you release pilot control then try again holding pilot down longer. If it still won't stay lit then thermocouple will need replace. Good luck. Thanks
I'm having the same exact problem... At first we thought was the vent... but the way the flames goes out... it seems that there is "not enough oxygen" more than "blown out by the wind"... right after both main & pilot goes out, I can't even light any external flame inside the chamber... and it doesn't feel like the outside cold air coming in... it just feel like there is some sort of gas in the chamber that's so strong, it prevents flame... and the only thing I can think of is that it doesn't have enough oxygen, but too much natural gas, and flame can't sustain.
If the burners do not fully ignite, the sensor will shut the furnace down. The lack of sufficient burner flame is a gas valve or gas pressure problem within the valve. Replacing the gas valve with the original one may get you going. I surely suggest a professional service company for safety reasons and a thorough inspection. A 20 year old furnace is past it's normal life span.
I have a Williams top vent gravity wall furnace (model 5009622) and I had the same problem. I had to take the cover off the furnace -- screw on top and two at the bottom (open the access door and there is one screw on each side) to get to the reset button for the vent safety shutoff system. On my furnace it's on the left side toward the top of the unit. I pressed the little red reset button and it's been working ever since. If your furnace is properly installed and doesn't have bird's nest in the chimney, it should work fine. Good luck!