Question about Honeywell Programmable Thermostat Heater
You are on the right track, however, the biggest problem I see is that the new Honeywell thermostat that you have is for a heat pump system and judging off your old thermostat, you don't have a heat pump. A heat pump system requires more wires and different terminals for the extra components it has like the reversing valve and such and since you don't have any of those, your thermostat is trying to tell the old unit to do things it simply cannot do. Your wire colors are correct as you described and on a standard thermostat you will have the same terminals as you do now. C/B(Blue)= is common by the way. One way to look at the RC/RH terminals is to think of it as both 24v, one being for heat(H), and one for cool(C). When they are jumped together, it allows the thermostat to use one wire for power instead of two (Red). Hope this helps and good luck!
Posted on Jul 14, 2010
RC - power for cooling
RH - power for heat
since you have only one transformer you need to put a jumper with this two terminals.
RC/RH - R ( power )
G - G ( fan relay)
W - Aux ( heat relay)
Y - Y ( cool relay )
this is so simple if the Honeywell thermostat is doing erratic operation maybe you need to reset the thermostat.
Posted on Sep 15, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 15, 2017 | White Rodgers Home Security
Aug 30, 2014 | Honeywell RTH3100C - Digital Heat Pump...
Jul 21, 2014 | Honeywell Th5220d1003 Non-programmable...
May 30, 2010 | Honeywell Electronic Programmable...
Jan 30, 2010 | Honeywell Electronic Programmable...
Nov 14, 2009 | Honeywell Programmable Thermostat Heater
Oct 16, 2009 | Honeywell Electronic Programmable...
Aug 12, 2009 | Honeywell Electronic Programmable...
Dec 20, 2008 | Honeywell Electronic Programmable...
Dec 20, 2008 | Honeywell Programmable Thermostat Heater
Jun 29, 2016 | Honeywell Programmable Thermostat Heater
Apr 27, 2016 | Honeywell Programmable Thermostat Heater
1,057 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: