Aprilaire 700 last winter and it worked great. This season I changed the wick and now all of a sudden the thing doesn't turn on no matter what I set it at, or what the humidity in the house is.
- If you need clarification, ask it in the comment box above.
- Better answers use proper spelling and grammar.
- Provide details, support with references or personal experience.
Tell us some more! Your answer needs to include more details to help people.You can't post answers that contain an email address.Please enter a valid email address.The email address entered is already associated to an account.Login to postPlease use English characters only.
Tip: The max point reward for answering a question is 15.
It appears your Aprilaire model 700 is wired to only operate when your HVAC fan is operated by your thermostat. Your HVAC installer can wire the humidifier control to operate the humidifier during a heat call, fan call or to turn on the fan when there is a need for humidification. Please contact your HVAC installer to have them change the wiring.
Thank you for giving us the opportunity to be of service Sincerely,
yes it should be bypass but solenoid could be trying to open but the voltage to it may be to low if you have 24v ac power at the 2 small wires. but to change shut down power to furnace and water to humidifier.you loosen the 2 compression nuts unwire they cant be reversed so dont worry then 2 mounting screws then reverse to install
reason why I asked they sometimes have a problem sensing current and you may need to wind the wire twice instead of one pass. If you jump the wires at the humidistat and the unit turns on its either the stat or you may want to do a relative humidity check on the house to see where your at
do you hear a clicking at the solinoid? grab the solinoid and turn it on to see if its getting voltage, you should feel it energize. you can turn off the water supply and disconnect the water line from the solinoid. there is a black pre screen inside the inlet if you have a tiny flat heat screwdriver insert it into the inlet and turn it out. clean it and retry. you can also make sure the orifice isnt clogged its located on the outlet side of the soliniod. when you remove you will probably have a stream of water come out of the feed tube thru the orifice, even if it has sat all summer. if water comes out you dont have a clogged orifice. donot try to **** out the orifice if its clogged you will need to get a new one fron www.aprilaire.com . you can verify it clogged by after cleaning the prescreen reconnect the water line inlet and turn on humidifier if water comes thru the solinoid with the outlet feed tube not connected then the orifice is clogged. If you clean the prescreen and the orifice is fine ,still no water then you will need a new solinoid you should also be able to purchase from aprilaire. here is links to the solinoid and orifice
The humidifier should not turn on untill the furnace blower starts. Since the fan stays on. does the solenoid valve also stay on? If they both stay on you probably have a bad humidistat. If only the blower stays on then the circuit bourd in the humidifier is defective.
sounds like either the motor is off balance
or is going bad again
either way id be on the phone to the guy who did the rapair
more than likely the set screw on the sqiral cage came loose and now its vibrating