Question about Heating & Cooling
First recommendation. Turn off the furnace, and buy some carbon monoxide detectors. I definitely do not recommend you using the furnace without them.
Yes, the heat exchanger can be replaced.
No, you would not want to attempt to braze the holes.
If the HE is cracked or has holes, it needs to be replaced. That can kill you.
They are usually removed by disassembling 90% of the furnace and part of the cabinet. This is a major repair, and not a do it yourself issue unless you have some experience and training in the operation of furnaces and electrical controls.
Also be aware that your HE may be under warranty depending on the age of the unit. Most are 10 year warranties. Some are even lifetime.
Posted on Dec 14, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 21, 2017 | Reddy Heating & Cooling
Aug 12, 2011 | Carrier Heating & Cooling
May 03, 2011 | Ford Ranger Cars & Trucks
Dec 18, 2010 | Reddy Heater RLP100 Portable Forced Air...
Jul 05, 2010 | Pentair Minimax Ch 400,000 Btu Propane...
Jan 25, 2010 | Williams 2509612 Ceramic Mid-Size Heater
Jun 07, 2009 | Dometic RM2652 Refrigerator
May 28, 2009 | Hayward H Series Pool & Spa Heater 400k...
Mar 23, 2009 | Desa International RCP25 Utility Heater
Dec 23, 2008 | Coleman Propane Forced Air Heater...
150 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: