Question about Kohler 12 kW Emergency Power System - 12RES-L
The generator was starting then shutting down after 20 seconds. yesterday the repairman replaced the govenor. today it starts but revs up and down then shuts down after 20 seconds. will continue to run if i hold the throttle steady. if i let go it revs up the down then shuts down. thoughts... will i damage it if i hold the throttle steady to keep it running,
What you need to know is there enough fuel going to the regulator. It should be 7 to 11 inches Water Column. If not your problem may be not enough fuel. That includes when the heater in your house kicks on and what ever gas appliance you may have. Once you verify that you need to figure out if you have the proper pressure coming out of the regular on the inside of the generator. Next I would look at compression of the cylinders. It may need new piston rings.
Posted on Oct 09, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 10, 2015 | Kohler Residential Standby Generator-14 Kw...
Sep 30, 2014 | Kohler Electrical Supplies
Jun 12, 2014 | Kohler Electrical Supplies
Oct 25, 2012 | Kohler 17RESL 17 kW Generator with 200 Amp...
Jul 11, 2012 | Kohler Electrical Supplies
May 28, 2011 | Kohler 12 kW Emergency Power System -...
Jul 22, 2010 | Kohler 12 kW Emergency Power System -...
Sep 24, 2009 | Kohler Electrical Supplies
Aug 08, 2009 | Kohler 12 kW Emergency Power System -...
638 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: