Question about York Yankees Bedding MLB Comforter
I have a York D3CG 60 and two D2CG 120 s that answer the heat call, but the burners only cycle one time then they blow cold air until i shut the units off and restart them
It could be that the flame is " Rolling out" of the burner compartment and hitting the safety device known as the "ROLL SWITCH" If this happens all the time you probably have a split / cracked heat exchanger or a heat exchanger that has holes in it. The holes allow the air pressure from the indoor blower to enter into the burner tubes and blow the flame back out of the burner compartment...not to mention allowing poisonous CO [ Carbon Monoxide ] to enter the air stream that goes into the heated space of the people down below. The holes don't have to be very big for this to happen and if the heat exchanger is split along the factory seam...it will be very heard to see unless you have the heat exchanger heated up for a while. Heat exchangers are the second most expensive part of a rooftop unit right after an A/C Compressor. they're not too difficult to change but you have to know what you're doing specifically when resealing all the sides and edges so CO doesn't leak out of a seam and kill everyone down below.
Posted on Mar 02, 2010
Whats happenening is that the unit's nare probably going off on the high limits. Thats when the fans will run until they are cycled off manually. Check yor filters and the belts to make sure that you are moveiong enough air for the unit. theanks for usin Fixya.
Posted on Dec 23, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 29, 2015 | Heating & Cooling
Dec 06, 2013 | Heating & Cooling
Feb 03, 2011 | AmcorAire UCHW-H12AF2 Split System Air...
Dec 05, 2009 | York Furnace Draft Inducer Blower Fasco #...
Oct 25, 2009 | York Yankees Bedding MLB Comforter
Jul 29, 2009 | Heating & Cooling
Jul 10, 2009 | York Yankees Bedding MLB Comforter
Apr 12, 2009 | Water Heaters
Jan 10, 2009 | York Yankees Bedding MLB Comforter
813 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: