Question about Carrier XHB123D X/Y Series Heat/Cool Air Conditioner
I have Carrier Weathermaster 8000 with ces0110057-02 control board.
When thermostat calls for heat, I hear click on the board, diffuser turns on, ignitor glows shortly after... and then NOTHING. I measure V across 2 terminals on gas valve as well as each terminal and ground. All measurements show 0V. Main blower works fine since I can turn my fan on and it runs. I checked 3A auto fuse on the board and it has not blown. I checked the wire terminals and nothing seems loose.
Do I have a bad board? If so, is it worthwhile to spend $$$ on the replacement board? My furnace is 13 years old.
Check the two wires coming directly off the transformer. They will be connected to the board the line voltage will be black and white and the 24voltage will be something like blue and red undo from board and check to see if you have 24 volts there. If not your transformer is bad 10 dollar part. Take it to Heating and Air parts house to replace. Let me know ken
Posted on Dec 13, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 26, 2015 | Heating & Cooling
Mar 02, 2015 | Heating & Cooling
Nov 28, 2011 | Goodman GMS90703BXA Heater
PROBLEM #1 - HOT SURFACE IGNITOR DOES NOT GLOW RED
(Remember to wait for purge time, 17/34 seconds, on models so equipped).
A. No main power
B. Faulty transformer
C. Faulty thermostat
D. Faulty limit switch
E. Faulty blower interlock switch
F. Faulty hot surface ignitor
G. Faulty ignition control
Perform normal system checks of main power, transformer, thermostat, limit
switch, blower interlock switch, and replace faulty component.
With power on and thermostat set at its highest position, check voltage
between "TH" and "TR" on HS780 ignition control. If 24 volts is not present
check output at transformer. If no, replace transformer. If transformer
checks out OK look at other controls in the 24 volt circuit I.E.: thermostat,
limit switch, blower interlock switch. Check for 120 volts between "neut"
(L2) and "120" (L1). Check for 120 volts at the ignitor across "IGN" and
"IGN" terminals on the HS780 ignition module. If 120 volts is present,
replace ignitor. If no, replace the 780 series module
PROBLEM #2 - IGNITOR GLOWS RED BUT MAIN BURNER
A. Improper ignitor alignment
B. Faulty ignition control
C. Faulty gas valve
D. High inlet gas pressure
E. Polarity reversed
F. No earth ground
Check for availability of gas at gas valve. Make sure the manual valve
upstream of the gas valve and the gas valve are in the full on position. Also
make sure gas is being supplied to the system at the proper pressure, too
high will lock-up the valve.
Check proper polarity of "NEUT" and "120" on the ignition control by reversing
the wires, if reversed gas valve will not open. If this does not solve the
problem, replace wires as they were.
Check for proper ignitor position.
Check for a good earth ground by using a meter connected between L1
and furnace chassis. Should read 120 volts, if no, check and/or repair ignition
ground wire or ignition control mounting screws.
CAUTION POLARITY MUST BE OBSERVED
Check for 24 volts at the gas valve terminals; "1" and "2" on a 7200 series,
"M" and "C" on a 7100 series, "TH" and "TR" on a 7000 series. If yes,
check wire integrity or change the gas valve. If no, change the 780 series
That is pretty much all of the troubleshooting required.
Thanks for choosing FixYa,
Feb 14, 2011 | Rheem 40 Gallon FVR NATGAS Low WATER...
Jan 03, 2011 | Heating & Cooling
Dec 11, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Oct 30, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Dec 06, 2009 | Heating & Cooling
Nov 12, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
386 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: