Question about Reddy Heating & Cooling
Heater motor would run but heater would not ignite. I took the bonnet off, cleaned the nozzel and the filter the comes from tank/line. When plugged in without bonnet, heater motor runs, ignites and heats fine. WITH BONNET ON HEATER motor runs but heater will not ignite. What is the problem? What can I do to fix it?
First, let me say that the general principal of fuel delivery ***to the spark plug*** depends on several things.
On your heater the first step is to set the air pressure to specs. Instructions are on the www.reddyparts.com website. This pressure setting directly affects fuel delivery & fuel atomization
This nozzle rule will only apply if everything is correct as far as fuel delivery applies. The pump pressure must be correct- not almost correct. Set the pressure with a low-pressure gauge that registers12-15 psi max. A gauge with a higher scale just will not read close enough to satisfy the system. If the pressure is not correct, the above rule will not apply. Instructions for setting the pressure can be viewed at http://reddyparts.com/pressure.htm.
Posted on Dec 12, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 11, 2012 | Reddy HEATER RLP30 30,000-BTU PORTABLE LP...
Here are a couple of tips that I wrote that tell you how to troubleshoot a Torpedo or Reddy heater...
Reddy Heater - Troubleshooting Torpedo Heaters
Feb 22, 2011 | Desa International R40 Utility Heater
Jan 06, 2011 | Reddy REDR40T Heater
Dec 23, 2010 | Reddy R155D Utility Heater
Oct 21, 2010 | Reddy Heater RLP100 Portable Forced Air...
Feb 05, 2010 | Reddy Heating & Cooling
Jan 15, 2010 | Reddy HEATER R115 115,000-BTU PORTABLE...
Jan 07, 2010 | Reddy Heater-170,000 BTU Kerosene Deluxe
Jan 24, 2009 | Reddy Heating & Cooling
Jan 07, 2017 | Reddy Heating & Cooling
349 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: