Question about Goodman Air Conditioners
Remove 1 of the 24volt wires from the transformer do you still have the problem? If you do reinstall the wire back to its terminal where taken loose then do the other wire. and see. If it shuts off with the red wire removed from the transformer 24 volt side the problem is a shorted wire from the furnace to the thermostat.
Posted on Dec 19, 2008
Tips for a great answer:
Feb 27, 2014 | Goodman Manufacturing Goodman...
Apr 20, 2013 | Air Conditioners
Feb 01, 2013 | Goodman Air Conditioners
Jul 17, 2011 | Air Conditioners
Aug 17, 2010 | Goodman CKL24AR24 Air Conditioner
Jun 06, 2010 | Goodman CLJ30AR32 Air Conditioner
Jan 03, 2009 | Goodman CLQ36AR49 Air Conditioner
Jul 03, 2008 | Goodman CLQ36AR49 Air Conditioner
Jun 01, 2008 | Goodman Air Conditioners
83 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: