Question about Goodman GMS90703BXA Heater
I am blessed to have a GMP125-4. A few months ago I replaced the induction motor. The furnace has been working fine up untill 2 days ago. When the unit begins its cycle, the induction blowwer kicks on and then nothing happens. It continues to run for ever. The HSI never turns on. If however, I kill the power to the unit then turn it on. It works fine untill it calls for heat again. I'm thinking its the circut board any other suggestions?
I'm sure you have since had this repaired and as a fellow Goodman 'blessed' I would appreciate reading your solution.
The condition you described could be caused by a failed relay or relay driver (transistor). Fortunately, the only problem we have had to date (~4 years) is a failed thermostat and a need for recharging of the AC coolant this last summer.
Posted on Sep 28, 2009
Pull the rubber hose off the pressure switch. and blow into the Induced draft motor housing if you cant you can pull the hose off the IDM and try to clear it with a small paper clip. reconnect and try again. you can also get the flash code off the board while the unit is running but not working.
Posted on Sep 18, 2009
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 15, 2017 | Heating & Cooling
Oct 22, 2016 | Heating & Cooling
Dec 31, 2014 | Heating & Cooling
Mar 14, 2014 | Bryant 352AAV036060 352AAV 60,000 BTU, 92%...
Jan 06, 2013 | Heating & Cooling
Apr 12, 2011 | Heating & Cooling
Jan 31, 2011 | Heating & Cooling
Mar 22, 2010 | Heating & Cooling
Nov 26, 2009 | York Yankees Bedding MLB Comforter
222 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: