Question about Goodman GDS80904BNA Open Flame Heater
The stat will click on indicating the furnace is on, when I go out to check the furnace the blower is all that is on. I can override it through the stat and get the burners to ignite but after about 5 to 10 minutes the furnace will turn off and the blower will remain on. The stat is set to 71 and the highest I can get the temp without overriding through the stat is 65. Usually wake up every morning with temp @64 or62. Like I said , burners will ignite, blower is working....is it the stat?
I don't think so. But you can test by jumping the stat wires and see what happens. What you really need to do is get in front of the furnace and jump it out at the furnace. Follow the sequence of operation and see where it is failing. Follow this sequence:
On a call for heat, the 24 volt thermostat sends a signal to the control module. The control module will indicate a call for heat with a light on the control either blinking or remain solid depending upon model. The inducer (exhaust) blower will purge all gasses from the furnace and pressurize a pressure switch. Once the pressure switch tells the module to continue, the electronic ignition will energize and send 120 volts to the ignitor. The ignitor will glow and you will be able to see it if viewed thru the small inspection port. Once the ignitor gets hot enough, it sends a signal to the module opening up the gas valve (24 volts). Either a pilot will come on or the burner tube will ignite then spread the flame to all burners. Lastly a safety sensor will be looking for a certain temperature within a few seconds and the furnace will continue to operate and the room air blower will turn on in a minute or two.
What could go wrong? The unit will not run if there is no signal from the thermostat (bad thermostat or broken wire), the control module does not sense a signal from the thermostat (bad control), the inducer does not energize (bad motor), the pressure switch does not close (blocked vent piping, bad switch, plugged condensate hose), the ignitor does not energize (bad control, bad ignitor), the gas valve does not open or there is no gas (bad gas valve, broken wire, no gas), the pilot does not lite (dirty pilot), the burner does not lite (bad burner, plugged orifice, not enough combustion air), the flame does not spread to each burner (bad flame spreader, dirty flame spreader, more bad burners), the flame safety sensor does not detect flame (dirty or bad flame spreader, bad flame sensor, broken wire, bad control), or the room air blower does not energize (bad fan motor, bad control).
Most newer furnaces will have a diagnostic center or control built into the control module. You may be able to view it as it is running thru a small viewing port. Some models will require the removal of an access panel prior to finding it. On the reverse of the access panel, there will be a diagnostic chart that will aide you in understanding any error code recorded (usually a blinking light).
Posted on Feb 20, 2009
This sounds like a pressure switch problem,alot of the time condensation gets into them and cause the problems you are describing...if you can take them off and shake upside down untill water is out of them...also check to see if anything is biocking intake or exhast
Posted on Dec 11, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 12, 2011 | Goodman GMS90703BXA Heater
Dec 19, 2009 | Goodman GDS80904BNA Open Flame Heater
Nov 20, 2009 | Goodman GDS80904BNA Open Flame Heater
Oct 14, 2009 | Goodman GDS80904BNA Open Flame Heater
Jun 02, 2009 | Goodman GMS90703BXA Heater
Mar 02, 2009 | Goodman GDS80904BNA Open Flame Heater
Dec 27, 2007 | Goodman GDS80904BNA Open Flame Heater
233 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: