Question about Goodman GMS90703BXA Heater
When i slide the thermostat up there is no spark , does this mean a fuse is blown. manually the fan works.
There shouldn't be any spark. These furnaces light the burners with a hot surface ignitor. Once electricity powers the hsi it will cause to get hot and glow bright orange. If this is not happening, you probably have a bad hsi. This is a common problem and easily resolved.
Posted on Oct 07, 2009
You may need to replace the ignighter!...easy fix! or what it really sounds like is your thermastat
Posted on Dec 11, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 10, 2013 | Heating & Cooling
Jan 10, 2013 | Heating & Cooling
Nov 19, 2012 | Heating & Cooling
Mar 02, 2012 | Empire ECS HearthRite HR18MN Heater
Jan 08, 2011 | Goodman GMS90703BXA Heater
Nov 19, 2010 | Heating & Cooling
On a call for heat, the 24 volt thermostat sends a signal to the control module. The control module will indicate a call for heat with a light on the control either blinking or remaing solid depending upon model. The inducer (exhaust) blower will purge all gasses from the furnace and pressurize a pressure switch. Once the pressure switch tells the module to continue, the electronic ignition will energize and send 120 volts to the igniter. The igniter will glow and you will be able to see it if viewed thru the small inspection port. Once the igniter gets hot enough, it sends a signal to the module opening up the gas valve (24 volts). Either a pilot will come on or the burner tube will ignite then spread the flame to all burners. Lastly a safety sensor will be looking for a certain temperature within a few seconds and the furnace will continue to operate and the room air blower will turn on in a minute or two.
What could go wrong? The unit will not run if there is no signal from the thermostat (bad thermostat or broken wire), the control module does not sense a signal from the thermostat (bad control), the inducer does not energize (bad motor), the pressure switch does not close (blocked vent piping, bad switch, plugged condensate hose), the igniter does not energize (bad control, bad igniter), the gas valve does not open or there is no gas (bad gas valve, broken wire, no gas), the pilot does not light (dirty pilot), the burner does not light (bad burner, plugged orifice, not enough combustion air), the flame does not spread to each burner (bad flame spreader, dirty flame spreader, more bad burners), the flame safety sensor does not detect flame (dirty or bad flame spreader, bad flame sensor, broken wire, bad control), or the room air blower does not energize (bad fan motor, bad control).
Oct 05, 2010 | Goodman GMS90703BXA Heater
Jan 10, 2010 | Goodman GMS90703BXA Heater
Nov 09, 2008 | Lite On Laars Lite 2 Heaters: 250,000BTU...
91 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: