Question about Dayton E52 Utility Heater
It worked one day, then the next, no spark. Any Ideas where to start?
Check to be sure the Ignition Device (transformer) is grounded, first, then see if power is going in to the Ignition control. If power is going in, but there is no spark from the coil wire, then the transformer is bad (replacement part number 102482-01).
There are other parts the can create a no-fire situation, such as a defective Safety Control (reset), Therefore you must troubleshoot to find the exact problem in order to avoid throwing parts at the unit.
Posted on Dec 11, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 11, 2011 | Dayton (3VE49) Oil Filled Liquid Fuel...
Dec 08, 2010 | Dayton Heating & Cooling
Jul 31, 2010 | Dayton Gas Furnace Heater
Jan 14, 2010 | Heating & Cooling
Jan 12, 2010 | Dayton E52 Utility Heater
Nov 26, 2009 | Dayton (3E379) Heater
Oct 23, 2009 | Dayton Gas Fired Heater LP TC200VA - Heats...
255 people viewed this question
Usually answered in minutes!