Question about American Standard Cambridge 5' Americast Bathtub w/ Grab Bar Drillings & Le
We had the "smoke" test done twice to test where leaks might be in our sewer system. None were found. The subject bathroom had an Americast Tub installed about 4 months ago. We didn't really notice the problem till the gas-forced-air heating system came on. The air intake for the central HVAC system is in the hall right next to the bathroom. Somehow, sewer gas seems to be getting sucked out of the OVERFLOW vent of the tub and is very strong. I removed the cover plate on the overflow and duct taped the hole completely. This seems to resolve the issue of the sewer gas. Any ideas what would produce this very strong odor? Any thoughts are appreciated.
Hello all, I have been renting a house for over two years and all of a sudden this really bad sewer smell and some type of brownish film goes around the drain almost up to the spout the smell or what ever it is even burns my eyes a bit,this has never happened before it is worse over night,, is this bad for our health, I bleach it about 10 times a day, can anybody please tell me what it is?
Posted on Aug 27, 2010
I've encountered this problem about 4 or 5 times. It has always been when there is more than one bathroom with more than one tub/shower. What has happened is that one tub/shower hasn't been used for a month or two and the water in the P trap evaporates and then the sewer gas or septic bed gas can come up the pipe into the room. If you have a sink, toilet, shower or any fixture that has a trap, make sure that you pour a cup of water down approx. 1 per month if your aren't using the fixture.
Posted on Nov 12, 2009
I can think of two possible solutions to this issue.
Posted on Dec 10, 2008
I am a plumber and I once dealt with a similar problem. As it turned out there was nothing wrong with the plumbing. Whoever installed the tub spout filled it with plumbers putty! The putty had begun to rot from constant moisture (I know it sound strange) and was giving off the most offensive, sewer gas like odor. The customer had had two other plumbers in before me and she said I couldn't leave until I solved her problem. Who would have thought of removing tyhe tub spout. I had to think outside the box - your problem may require out of the box thinking as well.
Posted on Jun 16, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 06, 2014 | Plumbing
Aug 26, 2014 | Kitchen Appliances - Others
Jun 15, 2014 | Plumbing
Jul 27, 2011 | Whirlpool Aquatic Infinity Ii 2 Tub...
Feb 09, 2011 | Home
Jan 31, 2011 | Kohler 1107-R-0 ProFlex Bath Tub with...
Nov 29, 2010 | Air Purifiers
Jan 20, 2010 | American Standard Cambridge 5' Americast...
4,312 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: