Question about Heaters
The first thing I would look for is a blockage in the gasline, or at the gas valve.
It sounds like you are not getting gas to the ignitor/burners. This would cause it to obviosly, not sense flame.
When a unit does not sense flame, it will shut of, and usually try again up to 5 times (depending on brand/model)
So here's what happens in that scenario.
Call for heat.
Inducer motor kicks on, the sensor detects the inducer motor is working, and the ignitor starts glowing/sparking (depending on type of ignitor)
It will then send gas through the gas valve and ignite.
If the flame sensor does not detect flame, the glow coil shuts down, the gas shuts off, the inducer shuts off and you get your error code.
(Some units will then send on the blower motor, and you have to cut power to reset.)
Do you have a copper line with natural gas?
If so, replace it with stainless steel or black iron.
Coper apearantly reacts with the aditives in natural gas and tends to form a gray ashy substance that builds up in the copper tubings walls and eventually cloggs gas valves.
At the inlet side of the gas valve, there should be a screen to catch such things.
Turn off the gas, turn of the power, and remove the gas line going to the gas valve. Look for anything clogging that area, also look for kinks in the gas line.
Remember to use a "flamable gas approved" pipe dope or thread tape when reinstalling the supply line.
Lets see what you find there and then we can continue the diagnostic if needed.
Posted on Dec 10, 2008
Tips for a great answer:
Nov 28, 2015 | Heaters
Jan 23, 2008 | Goodman GMS90703BXA Heater
Dec 25, 2013 | Mr. Heater MH170FAVT Open Flame Gas...
Nov 05, 2011 | Goodman GMS90703BXA Heater
Feb 09, 2011 | Dayton Gas Furnace Heater
Jan 24, 2011 | Goodman Heaters
Feb 11, 2010 | Coleman Heaters
Feb 02, 2010 | Heaters
Mar 08, 2009 | Goodman GMS90703BXA Heater
Oct 26, 2008 | Goodman GMS80903BNA Heater
Dec 05, 2016 | Dyna-Glo Heaters
122 people viewed this question
Usually answered in minutes!