Question about Heating & Cooling
Orange = O
Red = R (with existing jumper)
Black = C
Yellow = Y
White =W1 (Or AUG)
Green = blower wire (usually green, double check with schematic)
(Green should not go to the HP.)
Orange to HP
Red to red and to HP
black to blue (or C) and to HP
White to W
Yellow to HP. (It may also go to a "float switch" if installed. but that will just be a safety switch on the drain pan in case the line clogs and it overflows.)
The green is typically used for the blower motor. (furnace only)
The orange is used for the reversing valve. (changes from AC to heat, is located in the HP only)
Blue is typically used for common (or "C") but they may have changed it to black due to a broken wire, or other problems.
The only wires going to the HP should be
Orange should not be going to the furnace at all.
HP wiring should be
Orange to orange or O
Red to R or red
Blue/black to blue or C
Yellow to Y
Posted on Dec 10, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 03, 2017 | Honeywell Heating & Cooling
Jan 18, 2015 | Ruud Heating & Cooling
Nov 05, 2014 | Honeywell VisionPRO 8000 Programmable...
Dec 12, 2013 | Heating & Cooling
Dec 29, 2009 | Honeywell Electronic Programmable...
Sep 20, 2009 | Heating & Cooling
Apr 20, 2009 | Goodman CLQ36AR49 Air Conditioner
Dec 06, 2008 | Intertherm Heating & Cooling
Mar 25, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jan 07, 2008 | Goodman GMS90703BXA Heater
263 people viewed this question
Usually answered in minutes!