Question about Heating & Cooling
I need a Trouble shooting manual for Model# RGUJ-05EA-ER RHEEM electric ignition GAS FURNACE.
Igniter turns red hot but the Gas Valve just shakes and makes a clicking sound and then the ignitor will go out.
Furnace does not fire up and fan does not kick in.
Gas valve is Honeywell Part# VR8205A 2008 reg 3.5 ADJ 3-5 Range 24V 60HZ total current .5 A uses class 2 transformer.
I also do not see any type of control board with a digital read out flashing any error code. Please Help.
Check your voltage going into the gas valve. It should be 24-27 volts. If it is to low the gas valve will chatter. If the voltage is strong enough you have a bad gas valve.
Posted on Apr 03, 2009
replace the gas valve....test for 24volt at the gas valve input. if you have this then it's a def gas valve relay not working.
Posted on Dec 29, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 28, 2014 | Heating & Cooling
on Dec 03, 2009 | Heating & Cooling
Dec 29, 2012 | Bryant Single-Packaged AC & Gas Furnance...
Jan 16, 2010 | Heating & Cooling
Dec 30, 2009 | Heating & Cooling
Jul 02, 2009 | Ruud UBHC Air Conditioner
May 05, 2009 | Rheem Tankless Hot Water Heater...
Dec 09, 2008 | Heating & Cooling
May 24, 2017 | Honeywell Heating & Cooling
243 people viewed this question
Usually answered in minutes!