Question about Air Conditioners
I need a Trouble shooting manual for Model# RGUJ-05EA-ER RHEEM electric ignition GAS FURNACE.
Igniter turns red hot but the Gas Valve just shakes and makes a clicking sound and then the ignitor will go out.
Furnace does not fire up and fan does not kick in.
Gas valve is Honeywell Part# VR8205A 2008 reg 3.5 ADJ 3-5 Range 24V 60HZ total current .5 A uses class 2 transformer.
I also do not see any type of control board with a digital read out flashing any error code. Please Help.
Check your voltage going into the gas valve. It should be 24-27 volts. If it is to low the gas valve will chatter. If the voltage is strong enough you have a bad gas valve.
Posted on Apr 03, 2009
replace the gas valve....test for 24volt at the gas valve input. if you have this then it's a def gas valve relay not working.
Posted on Dec 29, 2009
Tips for a great answer:
Oct 25, 2013 | Rheem Packaged Gas And Electric Unit 13...
Oct 25, 2013 | Rheem Gas Furnace 125,000 BTU 80 AFUE....
Sep 24, 2013 | Ruud Rheem Weather King Furnace Igniter...
Dec 16, 2010 | Air Conditioners
Nov 20, 2009 | Carrier Air Conditioners
Oct 20, 2009 | Ruud UBHC Air Conditioner
Jul 02, 2009 | Ruud UBHC Air Conditioner
Dec 09, 2008 | Air Conditioners
Nov 23, 2007 | Carrier XHB123D X/Y Series Heat/Cool Air...
243 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: