Question about Heating & Cooling
I need a Trouble shooting manual for Model# RGUJ-05EA-ER RHEEM electric ignition GAS FURNACE.
Igniter turns red hot but the Gas Valve just shakes and makes a clicking sound and then the ignitor will go out.
Furnace does not fire up and fan does not kick in.
Gas valve is Honeywell Part# VR8205A 2008 reg 3.5 ADJ 3-5 Range 24V 60HZ total current .5 A uses class 2 transformer.
I also do not see any type of control board with a digital read out flashing any error code. Please Help.
Replace the gas valve....test for 24volt at the gas valve input. if you have this then it's a def gas valve relay not working.
Posted on Dec 29, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 28, 2014 | Heating & Cooling
Dec 05, 2013 | Heating & Cooling
Oct 23, 2013 | Rheem Classic Series 90%...
Sep 23, 2013 | Rheem Ruud Weather King Corsaire Rheem...
Dec 20, 2012 | Heating & Cooling
Mar 11, 2011 | Heating & Cooling
1,334 people viewed this question
Usually answered in minutes!