Question about Air Conditioners
The condensate drain line is probably clogged.
Find out where the pipe exits the home, and attatch a wet/dry shop vack to the end of the drain line, close it up around the pipe as much as possible and trun it on.
These typically get clogged with dust, dirt, pet hair, mold etc.
They usually clog at the elbows, P-traps and the inlet coming from the drain pan. There is an internal drain pan in the unit that catches the condensation. When the line clogs the pan overflows and you have water dripping from the unit.
There is also a small chace the pan has a hole in it, but thats fairly rare. There is also a chjance that if the unit is not level the water will overflow the pan before it can drain. (most pans are only 1 to 2 inches deep.) Make sure the unit is level or veryslightly lower toward the drain side.
Posted on Dec 10, 2008
Tips for a great answer:
Jun 27, 2011 | Air Conditioners
Mar 04, 2011 | Coleman Air Conditioners
Jan 12, 2011 | Air Conditioners
Dec 26, 2010 | Fujitsu Air Conditioners
Jun 14, 2010 | Fedders A6X05F2G Wall/Window Air...
Sep 01, 2009 | Air Conditioners
Jun 08, 2009 | Dometic Rooftop RV Air Conditioner
May 28, 2009 | Goldstar R5050 Air Conditioner
Apr 29, 2009 | Samsung AW0503B Air Conditioner
Dec 05, 2016 | Air Conditioners
409 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: