Question about APC Matrix-UPS 5000 UPS System
Inherited a four year old Matrix 5000 with a control unit and 5 battery units. Panel reads "no battery communications" but the UPS appears to be functioning for at least short power outages. Do we need new batteries?
You will get that message when the communications cable is not hooked up. It looks like a phone line and daisy chains from one battery to another and ends at the Matrix Control unit. If you have those installed and it still says no communication the system need service.
If you have a volt meter you can check the voltage from each battery at the plug. It should be 48 volts or more, usually on a fresh battery pack it will read 54.0+ volts.
Hope this helps,
Posted on Jan 04, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 03, 2017 | Maytag Microwave Ovens
Jul 13, 2011 | Admiral Refrigerators
Jan 24, 2011 | Heating & Cooling
Mar 16, 2010 | APC Matrix-UPS 5000 UPS System
Dec 27, 2009 | APC Matrix-UPS 5000 UPS System
Jul 30, 2009 | APC Matrix-UPS 5000 UPS System
Apr 23, 2009 | APC Matrix-UPS 5000 UPS System
Jan 10, 2009 | 2005 Nissan Altima
Dec 15, 2007 | Jenn-Air SVE47100 Slide-In Electric...
Apr 25, 2013 | APC Matrix-UPS 5000 UPS System
476 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: