Question about Your One Source 100 Amp Main Lug Load Center
I just installed a new QOC20U100F panel & the power surges (lights flicker) with the breaker in #7 & #19. When I move the breaker (hot attached) to any other location it works fine. Does this mean the panel is defective? Thanks
Not likely check the neutrals on those circuits the chance that 7&19 are bad and everthing in between is good is almost impossible. i would check the wires very close and also inspect the neutral buss connections both main connections and circuit connections
Posted on Dec 09, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 21, 2015 | 2007 Pontiac G5 Gt Coupe
Mar 03, 2015 | Fisher and Paykel Washing Machines
Jun 05, 2017 | Jenn-Air Ovens
Jan 14, 2014 | Jenn-Air Ovens
Nov 25, 2013 | Proform 625 Front Roller Model Pftl62510
Aug 21, 2010 | Your One Source 100 Amp Main Lug Load...
Aug 01, 2010 | Brother MFC-8480DN All-In-One Laser...
Jul 31, 2010 | 2004 Ford Taurus
Apr 15, 2009 | Kitchen Appliances - Others
Feb 16, 2009 | General Electric 20 Amp, 1 Pole Thick Type...
Feb 23, 2018 | Subaru Electrical Supplies
77 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: