Question about Fahrenheat Electric Convector Baseboard Heater, 3'
Posted by dogmanwayne on Dec 07, 2008
I am installing a noma 1000 watt heater. Controller is a line Noma line voltage double pole thermostat, wiring 12\2, breaker double 20\20. I am not getting heat. The red\black are from the breaker to line at each thermoatate terminal, load is again black\red from each terminal. At the heater I am getting 120 volts at each wire red and black. The black is connected to the black of the heater and the red to the white at the heater by wire nuts and the copper to ground. With the thermostat on I am getting no heat... I thought it might be a defective heater and exchanged it... the same problem. Any ideas? Thanks Wayne
First, is this a 120 VAC or 240 VAC heater? 120 VAC heater will usually have one Black & one White wire and 240 VAC heater will usually have two Black wires or one Black & one Red wire. If it is a 120 VAC heater then you need to supply the white wire at the heater with a neutral (white) wire from the breaker panel. If it is a 240 VAC heater then you need to verify that you have 240 VAC at the heater from Black lead to Red lead. If you are not sure about how to do this please have an experienced electrician look at it so you don't get electrocuted and/or burn up your new heater. Hope this helps!
Posted on Dec 10, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 14, 2014 | Honeywell Heating & Cooling
Mar 20, 2013 | Hardware & Accessories
Jan 23, 2013 | Solar Noma 7 Day, 6 Event Outdoor Timer -...
Dec 04, 2012 | Hardware & Accessories
Dec 11, 2011 | Hardware & Accessories
Oct 03, 2011 | Solar Noma 7 Day, 6 Event Outdoor Timer -...
Aug 19, 2011 | Hardware & Accessories
Feb 14, 2010 | Honeywell Electronic Programmable...
Nov 12, 2009 | Heating & Cooling
Oct 04, 2009 | Fahrenheat Built-In Baseboard Thermostat...
Sep 16, 2010 | Fahrenheat Electric Convector Baseboard...
395 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: