Question about Reddy Heater-70,000 BTU Kerosene w/T'stat
Hsi igniton type.heater start up and runs normal for 30 seconds or so and shuts off? photo sensor bad? no repair attempt made yet and would rather diagnose the problem before throwing parts at it. can the blue wires be bypassed? i already know my thermostat control has a dead spot that won't work in part of the lower setting position but could this be gone completely now? or can it be bypassed?when turned all the way up heater still starts shuts off then must unplug and retry then will run again for 10 to 30 sec. no other symptoms no smoke or excessive fumes from heater. the problem just started all of a sudden after using heater in the garage for 6 hours. and yes it has fuel in it lol... any help would be greatly appreciated. thanks.
I would think that your photocell is bad.... or if your heater has a circut board... the relay or the board could be bad... i dont believe that is is your thermostat for the reason that it will still fire up even though it doesnt run very long... usually they just randomly stop running because the photocell is not detecting a strong enough flame... you could try turning your pump pressure up to get a better flame and see if that solves your problem... the pump adjustment screw is is located in the plastic cover on the back of the pump on the back of the electric motor... it takes a straight head screw driver to adjust...
Posted on Dec 27, 2010
I would say the thermostat is bad after reading your problem over several times. There is no reason to suspect a wiring problem, and I strongly suggest you don't bypass anything! A fire or explosion could result. Replace the thermostat as a probable cause.
Posted on Dec 09, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 27, 2014 | Reddy Heater-30,000 BTU Propane Forced-Air...
Feb 21, 2011 | Desa International Reddy Heater R200BT...
Dec 01, 2010 | Reddy Heater-30-55,000 BTU Variable
Oct 21, 2010 | Reddy Heater RLP100 Portable Forced Air...
Jan 15, 2010 | Reddy HEATER R115 115,000-BTU PORTABLE...
Jan 11, 2010 | Reddy Heater-30-55,000 BTU Variable
Jan 27, 2009 | Reddy Heater-30-55,000 BTU Variable
Jan 23, 2009 | Reddy Heater-170,000 BTU Kerosene Deluxe
Dec 04, 2008 | Reddy Heater-30-55,000 BTU Variable
Nov 23, 2013 | Reddy Heater-70,000 BTU Kerosene w/T'stat
652 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: