Question about Water Heaters
Model N9MP1- one year old
when i call for heat the furnace will start,light up, and blow hot air for a few minutes then shut down. it will continue over and over until it has reached the set temperature.
Is installed in a vertical up flow or horizontal position , if in horz position you could have a bad or miss positioned roll out switch this is a thermal switch positioned toward the burner edge that if the flame rolls out of burner area trips and then resets as it cools allowing the furnace to re-start until it reaches temperature , something to check .
Posted on Dec 09, 2008
Tips for a great answer:
Nov 02, 2015 | Honeywell RTH6350D1000 5/2Day Prog...
Jan 31, 2015 | Water Water Heaters
Sep 12, 2014 | Rinnai Water Heaters
Mar 21, 2014 | Water Heaters
Aug 09, 2011 | Reliance Natural Gas Water Heater Control
Dec 30, 2010 | Water Heaters
Dec 09, 2010 | Whirlpool Water Heaters
Jan 03, 2010 | Calvin Klein The Field Controls Company...
Mar 16, 2009 | Honeywell Water Heaters
Nov 19, 2008 | Water Heaters
523 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: