Question about Water Heaters
Model N9MP1- one year old
when i call for heat the furnace will start,light up, and blow hot air for a few minutes then shut down. it will continue over and over until it has reached the set temperature.
Is installed in a vertical up flow or horizontal position , if in horz position you could have a bad or miss positioned roll out switch this is a thermal switch positioned toward the burner edge that if the flame rolls out of burner area trips and then resets as it cools allowing the furnace to re-start until it reaches temperature , something to check .
Posted on Dec 09, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 02, 2015 | Honeywell RTH6350D1000 5/2Day Prog...
Jan 31, 2015 | Water Water Heaters
Sep 12, 2014 | Rinnai Water Heaters
Mar 21, 2014 | Water Heaters
Aug 09, 2011 | Reliance Natural Gas Water Heater Control
Dec 30, 2010 | Water Heaters
Dec 09, 2010 | Whirlpool Water Heaters
Jan 03, 2010 | Calvin Klein The Field Controls Company...
Mar 16, 2009 | Honeywell Water Heaters
Nov 19, 2008 | Water Heaters
523 people viewed this question
Usually answered in minutes!