Question about Intertherm P3RA-048K Air Conditioner
It sounds to me like the motor itself is going off on its overload protection. taking the panels off may be allowing it to stay cool a little longer. also it sounds like the first guy replaced some type of temp. sensor.
Posted on Dec 10, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 20, 2014 | Intertherm Heating & Cooling
Dec 05, 2010 | Heating & Cooling
Aug 08, 2010 | Intertherm P3RA-048K Air Conditioner
Jan 11, 2010 | Intertherm Heating & Cooling
Oct 20, 2009 | Intertherm P3RA-048K Air Conditioner
May 07, 2009 | Intertherm P3RA-042K Air Conditioner
Dec 06, 2008 | Intertherm Heating & Cooling
Oct 14, 2008 | Intertherm Heating & Cooling
154 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: