Question about Intertherm P3RA-048K Air Conditioner
It sounds to me like the motor itself is going off on its overload protection. taking the panels off may be allowing it to stay cool a little longer. also it sounds like the first guy replaced some type of temp. sensor.
Posted on Dec 10, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 09, 2016 | Intertherm Heating & Cooling
Nov 20, 2014 | Intertherm Heating & Cooling
Feb 12, 2014 | Ruud RGTC07ERBGS N/A Achiever 75000 BTU...
Sep 20, 2011 | Water Heaters
Feb 20, 2011 | Echo Back Pack Blower Rack Fits Stihl...
Dec 05, 2010 | Heating & Cooling
Oct 29, 2009 | Heating & Cooling
Oct 20, 2009 | Intertherm P3RA-048K Air Conditioner
178 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: