Question about Aprilaire 600 Humidifier
My Aprilaire 600 appears to be operating properly, however,the humidistat never registers above a "1". FYI-The unit is attached to the intake ductwork and the humidistat is also mounted on the intake ductwork.
There are 3 things to check on the humidifier. Check the metal mesh screen, is it wet after the humidistat is call? If it is dry the water solenoid my not be opening or the nozzle is plugged. The circulating fan blows air through the wet screen to add humidity. Does the fan spin when the humidistat is calling? There is an intake and exhaust on the humidifier. Check that the metal was cut out properly when the humidifier was installed to allow air to feely circulate?
Posted on Sep 24, 2007
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 24, 2017 | Aprilaire 400 Humidifier
Jan 20, 2011 | Aprilaire 400 Humidifier
Mar 03, 2010 | Aprilaire 600 Humidifier
Dec 03, 2009 | Aprilaire 700 Humidifier
Nov 28, 2009 | Aprilaire 600 Humidifier
Nov 27, 2009 | Aprilaire 600 Humidifier
Jan 12, 2009 | Aprilaire 600 Humidifier
Aug 27, 2008 | Aprilaire 600 Humidifier
May 22, 2017 | Aprilaire 600 Humidifier
372 people viewed this question
Usually answered in minutes!