Question about Air Conditioners
Grounded or shorted compressor. remove power. remove compressor leads and tape off . does breaker stop tripping? if it stays set on, then compressor is gounded or shorted. if it still trips then wiring or condensor fan is shorted or grounded, remove wires there and test same way . the item you disconnect that keeps breaker from tripping is your shorted or grounded item. usually the compressor. time for all new 410 a equipment. r22 is obsolete and out of production next year and equipment, and oils ,and gases dont mix at all. it must be all or nothing. don't invest a big cash repair in something unusable in a few years. good luck.
Posted on Dec 07, 2008
Tips for a great answer:
Nov 21, 2014 | GE Carrier Bryant Payne 1/3 Hp 115v Blower...
Jun 15, 2008 | Amana Air Conditioners
Nov 13, 2014 | Goodman Manufacturing Goodman ARUF48D14...
Mar 08, 2013 | Air Conditioners
Feb 03, 2013 | Intertherm E3EB-017H Furnace 17Kw 2
Jan 31, 2011 | Goodman CKL60AR60 Air Conditioner
Dec 07, 2010 | Air Conditioners
May 20, 2010 | Goodman CLQ36AR49 Air Conditioner
Jan 10, 2010 | Amana PTH123B25AJ Heat Pump Air...
Oct 09, 2009 | Air Conditioners
93 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: