Question about Heating & Cooling
Grounded or shorted compressor. remove power. remove compressor leads and tape off . does breaker stop tripping? if it stays set on, then compressor is gounded or shorted. if it still trips then wiring or condensor fan is shorted or grounded, remove wires there and test same way . the item you disconnect that keeps breaker from tripping is your shorted or grounded item. usually the compressor. time for all new 410 a equipment. r22 is obsolete and out of production next year and equipment, and oils ,and gases dont mix at all. it must be all or nothing. don't invest a big cash repair in something unusable in a few years. good luck.
Posted on Dec 07, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 21, 2014 | GE Carrier Bryant Payne 1/3 Hp 115v Blower...
Jun 15, 2008 | Amana Heating & Cooling
Nov 13, 2014 | Goodman Manufacturing Goodman ARUF48D14...
Nov 11, 2014 | Heating & Cooling
Jan 06, 2014 | Electrical Supplies
Mar 01, 2017 | Haier Energy Star ESA3183 Air Conditioner
Feb 03, 2013 | Intertherm E3EB-017H Furnace 17Kw 2
Dec 07, 2010 | Heating & Cooling
May 06, 2009 | 1999 Mercury Cougar
Mar 12, 2009 | 1992 Mercedes-Benz Mercedes Benz 300 Class
93 people viewed this question
Usually answered in minutes!