Question about Electrical Supplies
Just had the downstairs loo re-plastered - plaster removed the ceiling light and the wiring from the junction box - he had no idea how to reconnect the light.
So above the light I have a connector (a) with red, green and black wires going into it and coming out of it - assuming this is part of the ring.
The pull switch had a black and red wire going into it and at the moment the other end of this wire is floating next to where the light should be.
Can I run a black from connector (a) direct to the light and then run a red from connector (a) to the light via the pull switch? So in effect making a loop?
Any help would be appreciated.
Yes, run a black wire from connector (a) to one terminal of your new light fitting if you are installing a metal fitting you will need to connect an earth wire also.
If you are reusing the same pull switch and it is still connected as you describe then the floating end near the light is probably the switched live conductor, so you could connect this to the live terminal of the new light. but be careful it may be live.
Caution always disconnect the power before working on electrical wiring.
Please remember to rate this solution.
Posted on Dec 07, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 21, 2015 | Home
Nov 02, 2012 | Computers & Internet
Sep 14, 2010 | Toto Round Carusoe Two Piece Toilet, 1.6...
Nov 11, 2009 | Kitchen Appliances - Others
355 people viewed this question
Usually answered in minutes!