Question about Amana Heating & Cooling
Ok try this. Take a small diameter wire about 6 inches long. Go down to the furnace and remove the bottom panel. locate where the thermostat wires go into your unit and with a small screw driver place the jumper wire the 6" one and place it on red and white leave the other wires in place including the white and red ones. replace the bottom panel unit should start immediately. If it does you just solved the problem t-stat is bad. Now if the clicking starts and doesn't start the pilot your problem is gas valve related. This is another thing to check. You have a flame proving device located at the last burner looks like a thick piece of wire. Take some steel wool and very gently clean the surface to remove the carbon that has built up on it. Try this first as it is easy to see if the flame proving device was dirty. let me know ken
Posted on Dec 07, 2008
I really don't know a whole heck of a lot about this kind of stuff. The thermostat is made by Honeywell and it digital, not sure of the age. I don't think it is a t-stat problem, bc as I investigated a little further, there seems to be a "clicking" noise associated at the unit. I removed the bottom panel of the unit and there is a switch on the left side that remains depressed when the panel is inserted and closed. this seems to be the source of the "clicking". Forgive my ignorance, but does that give more insight to what the issue could be?
Posted on Dec 07, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 04, 2015 | Amana PTH123B25AJ Heat Pump Air...
Oct 10, 2008 | Amana PTH123B35AE Air Conditioner
Nov 05, 2014 | Honeywell VisionPRO 8000 Programmable...
Mar 19, 2013 | Heating & Cooling
Apr 10, 2011 | Heating & Cooling
Mar 06, 2010 | Amana Haier AP125HD Air Conditioner
Feb 11, 2009 | Ruud Central System Air Conditioner
Nov 15, 2008 | Amana Heating & Cooling
246 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: