Question about Heating & Cooling
I just installed a new programable hunter model 44110 thermostat and the fan will start but the compressor will not
the old thermostat was a carrier model hh01ad042 the only issue i had some question on was on the old carrier unit the red wire (R) was jumped to a terminal marked with the number (4)
all other conections were normal
green = G = fan
yellow = Y = compressor
white = W = heating
Do I leave the jumper in place on the new hunter unit, remove it, or something else?
With the jumper inplace does the compressor start? What about without? Unless you have more than one transformer you should leavethe jumper.
Posted on Dec 06, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 15, 2015 | Hunter Fan Company 7-day programmable...
Apr 23, 2008 | Hunter Fan Company 5/1/1 Programmable...
Aug 24, 2013 | Heating & Cooling
Jun 30, 2009 | Heating & Cooling
Mar 08, 2009 | Hunter Fan Company 5/1/1 Programmable...
Jul 04, 2008 | Hunter Fan Company 5/1/1 Programmable...
Jul 03, 2008 | Hunter Heating & Cooling
402 people viewed this question
Usually answered in minutes!