Question about Intertherm Heating & Cooling
Make sure fan relay is wired correctly (G) wire. Ensure the fan on therm is not on, it should be on Auto or off.
If your furnace is short cycling because it has to keep heating your home, the delay in the control board may be staying on to compensate for the exchangers getting hot. If it heats normally, then put your attention to your thermostat.
Set the heating system on aux heat only. Fan should not be on, if it does stay on after a heating cycle, see if the furnace is heating normally, and reaching temp as desired before the heat comes off. Then check the therm wiring, pull the face of the therm, disconnect green wire (fan) and try the heating again.
Posted on Dec 06, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 02, 2016 | Heating & Cooling
Jan 02, 2011 | Intertherm P3RA-048K Air Conditioner
Jan 06, 2010 | Ruud UBHC Air Conditioner
Oct 28, 2009 | Intertherm Heating & Cooling
Oct 20, 2009 | Intertherm Heating & Cooling
May 13, 2009 | Dometic Rooftop RV Air Conditioner
Apr 05, 2009 | Intertherm P3RA-048K Air Conditioner
Jun 14, 2008 | Ruud UBHC Air Conditioner
Jun 08, 2008 | Honeywell Heating & Cooling
170 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: