Question about Air Conditioners
If you have a volt meter, check to see if you have 24 volts coming from the thermostat on the yellow wire.
If you do, and it is set on emer heat, you have a bad T-stat.
It looks like it is wired properly.
If you have no meter, you could try changing the stat, I reccomend Honeywell or white rodgers.
Let me know if you eliminate the Tstat as the problem and we can go from there.
Chances are its the stat.
Posted on Dec 12, 2008
Tips for a great answer:
Jan 01, 2015 | Goodman Manufacturing Goodman GPH1348M41 4...
Feb 27, 2014 | Goodman Manufacturing Goodman...
Jan 23, 2013 | Goodman Manufacturing GPG1342090M41...
Jun 14, 2011 | Air Conditioners
Mar 01, 2011 | Bryant Air Conditioners
Jun 30, 2009 | Goodman Air Conditioners
Dec 18, 2008 | Air Conditioners
Nov 29, 2008 | Air Conditioners
192 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: