Question about APC Smart-UPS 3000R3BX (SU3000R3BX135) UPS System
The APC Smart UPS 3000VA had dead batteries, and I replaced them with new ones. After replacing the batteries, I tested the unit with a 100W load (light bulb), and it switches to battery mode properly with cut AC. Once the load is increased to 300W (halogen bulb again) it reports low battery, even when the AC power is present. The unit properly switches to battery power on AC loss, but low battery is still on. Once the load is decreased, the low battery goes off instantly and it works normally. I checked the battery voltage and I found 26V (2X13V) with 300W load (or no load) and AC power, and 23.5V (2X11.75V) when operated on battery with cut AC and 300W load, which seems OK. This problem is equal to one previous one but another model wanted to know as it is the solution
Let the ups be turned on just charging the batteries, u can have the voltage but the batteries still not fully charged. good luck
Posted on Feb 27, 2007
Tips for a great answer:
Jan 12, 2015 | APC Smart-UPS RT 3000VA UPS System
Feb 24, 2014 | APC Smart-UPS RT 3000VA UPS System
Jan 22, 2014 | APC Smart-UPS SUA3000RM2U 3000VA USB &...
Nov 13, 2013 | APC Smart-UPS RT 3000VA UPS System
Aug 03, 2011 | APC Smart-UPS RT 5000VA (SURTD5000XLI) UPS...
Jun 14, 2010 | APC Smart-UPS 1500VA Shipboard...
Aug 07, 2009 | APC Smart-UPS RT 3000VA UPS System
Sep 03, 2008 | APC Smart 3000VA (sua3000r2x145) UPS...
746 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: