Question about Heating & Cooling
95% chance that the heat relay is stuck closed (on)
You can disconnect power, locate the heat relay, see if you have continuity between the two leads on the load side of the relay. (with the two wires off)
If you do, the relay is stuck. Sometimes you can lightly tap the relay and it will unstick, but chances are it will just stick again soon.
If the relay is stuck/sticking, it needs to be replaced.
They usually run anywhere from 6 to 26 bucks at the local HVAC supply house.
Posted on Dec 06, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 14, 2015 | Honeywell Heating & Cooling
Sep 30, 2015 | Heating & Cooling
Oct 08, 2012 | Coleman Mobile Modular Home Electric...
Dec 21, 2010 | Heating & Cooling
May 31, 2010 | Heating & Cooling
Feb 11, 2010 | Heating & Cooling
Oct 17, 2009 | Intertherm P3RA-048K Air Conditioner
May 14, 2009 | Heating & Cooling
Mar 28, 2009 | Carrier Heating & Cooling
Jan 27, 2009 | Heating & Cooling
117 people viewed this question
Usually answered in minutes!