Question about Heating & Cooling
You have some limit switches located around the unit one high one or two around the middle one of them is opening and not closing. You need to take off the cover and locate the limits undo the wires and ohm them out you should have complete circuit now the one that is open when you find it is bad and needs to be replaced with the same rated heat temperature as original. Your t-stat goes through these limits and one open would kill the whole circuit. Let me know how it goes. ken
Posted on Dec 07, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 12, 2017 | Heating & Cooling
Jan 10, 2017 | Blue Flame Heating & Cooling
Jan 08, 2017 | Heating & Cooling
Jan 07, 2017 | Williams Heating & Cooling
Jan 07, 2017 | Heating & Cooling
Jan 06, 2017 | Majestic Heating & Cooling
Jan 04, 2017 | Heating & Cooling
Jan 03, 2017 | Coleman Heating & Cooling
Nov 03, 2014 | Heating & Cooling
Jan 01, 2014 | Williams (5009622) Ceramic Gas Wall...
Feb 23, 2017 | Heating & Cooling
101 people viewed this question
Usually answered in minutes!