Question about Heating & Cooling
You have some limit switches located around the unit one high one or two around the middle one of them is opening and not closing. You need to take off the cover and locate the limits undo the wires and ohm them out you should have complete circuit now the one that is open when you find it is bad and needs to be replaced with the same rated heat temperature as original. Your t-stat goes through these limits and one open would kill the whole circuit. Let me know how it goes. ken
Posted on Dec 07, 2008
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Dec 08, 2015 | Williams Heating & Cooling
Dec 30, 2014 | Williams Heating & Cooling
Feb 26, 2013 | Williams (5009622) Ceramic Gas Wall...
Jun 19, 2011 | Williams 3003622 Ceramic Wall Mounted...
Feb 27, 2011 | Williams Heating & Cooling
Nov 11, 2010 | Williams 6508732 Gas Heater
Jan 08, 2010 | Williams 2509612 Ceramic Mid-Size Heater
Jan 01, 2010 | Williams Heating & Cooling
Dec 22, 2009 | Williams 3003622 Ceramic Wall Mounted...
105 people viewed this question
Usually answered in minutes!