Question about Goodman CLQ36AR49 Air Conditioner
I installed a goodman 2 ton heat pump 2 months ago. heat and cool mode works fine but will not go into defrost. installed a new defrost board today still does not work. checked voltage at the condencer and air handler the thermostat wires have at least 24 volts at each wire . what could be the problem? thanks Tim
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 21, 2015 | Heating & Cooling
Jan 08, 2015 | Goodman Manufacturing Goodman GPH1543M41...
Sep 12, 2013 | Goodman Heating & Cooling
Jan 04, 2011 | Heating & Cooling
Jun 26, 2010 | Goodman CLQ36AR49 Air Conditioner
May 04, 2010 | Goodman CLQ36AR49 Air Conditioner
Nov 01, 2009 | Goodman Heating & Cooling
Sep 19, 2009 | Goodman CLQ36AR49 Air Conditioner
Jun 23, 2009 | Goodman CLQ36AR49 Air Conditioner
Jun 11, 2009 | Goodman Heating & Cooling
476 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: