Question about Heating & Cooling
If its a mercury bulb stat it must be perfectly level. or it will overshoot or under shoot depending on which way it is out of level. the heat anticipator under the cover if its an older stat should be .4 to .6 or it will over shoot. that is what lets it know that by the time it shuts off burner or strips and cycles down the fan it should be at the desired temp. if its digital be sure the hole in the wall behind it is sealed 100 percent. even a little cold or warm air leaking into the back of the stat can cause faulty readings and over or under temps. if this doesn't correct the stat itself may be bad and in need of new. good luck.
Posted on Dec 05, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 17, 2016 | Heating & Cooling
Nov 12, 2015 | Hunter 44860 H Univ. Touchscreen...
Sep 21, 2014 | TurboChef TORNADO Electric Oven
Jun 17, 2011 | Heating & Cooling
Apr 01, 2011 | Heating & Cooling
Dec 30, 2009 | Honeywell Programmable Thermostat Heater
Oct 22, 2009 | Panasonic Panafax UF-550 Plain Paper Laser...
Jul 22, 2009 | Honeywell Heat/Cool Thermostat
Apr 26, 2017 | Heating & Cooling
45 people viewed this question
Usually answered in minutes!