Hi sir my name is mr thomas, and i just recieve and answer from u about the lock door,and u said the temperature proble had blown,but how do i fix that or what else or where this proble is located.I need something more like suggestions.
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need. goodluck!
- If you need clarification, ask it in the comment box above.
- Better answers use proper spelling and grammar.
- Provide details, support with references or personal experience.
Tell us some more! Your answer needs to include more details to help people.You can't post answers that contain an email address.Please enter a valid email address.The email address entered is already associated to an account.Login to postPlease use English characters only.
Tip: The max point reward for answering a question is 15.
You need to answer in the original post as a COMMENT to Mr Colton's reply to you. If you do it that way, Thomas Colton Jr will get a notification that he has a reply to answer. Your way of making a reply does not work as Fixya gets 7 million enquiries a year, so it is impossible for one person to see even a fraction of them.
Mr Thomas, this code means Fixing error, firsf switch on your Photocopier Machine then press 1,0,8,7 again 1,0,8,7 display will change will show u000. then press 1,6,3 press start key two times. machine will go off and on again. try that ,if will not work i will give you onather way.
mr Slim A control R407c & R410a systems. P6 = indoor coil frost protection in cooling or indoor coil overheat protection in heating.
Cooling One of the 2 indoor coil sensors reads minus 15 deg C for 3 mins. Heating One of the indoor coil sensors reads over 70 deg C.
If you are sure the refrigerant charge is correct & system operation is correct then it could be a coil temperature sensor reading wrong temperature. If you have one of those little monitor things which plug into the outdoor circuit board you can monitor the indoor coil temperature. On later type remote controllers you can get all operating data like temp sensor data but you will need a service manual to do this. Or you can measure the ohms resistance of the temp sensors & compare with the chart in the service manual. if you can do it by yourself do if not then contatct ot mitsubishi maintenance personnnel for furhter action,
hope answer the question
sir,iam gopinath.i gave my handset in ur service centre on 29 feb,2008 with the job no 114-08-01148-001 in UCOM TECHNOLOGIES VIJAYAWADA ANDHRA PRADESH. the model of that handset is A1200 with the problem ear piece volume not obtain.daily they are postponing the part is not available. i just call to the some officer his name PAUL(9391370750) on 4th mar,2008 he said i will call you within 24 hrs.he does't call me and he does't receive my calls.then i call to the customer care (011-39026686) i make a lot of calls to them.my complaint no is 080607008754. Then they call me after 48 hours and said we send the part go and collect ur mobile after 2days.I go and ask my mobile they replied that the part is not available.Again i gave a complaint in ur costumer care centre and my complaint no 080619012373. sir when will u rectify my problem i purchase my mobile for rs.14000/- . Is i purchase my mobile to kept in ur service centre for demo or for show.i u say yes means i will leave.i want rs.5000/- for making calls to ur service centre and to ur costumer care and i waste alot of petrol in wandering ti ur service centre and i want the new replacement of that mobile because ihave warranty. otherwise i claim a case about on your service centre.please reply soon as soon as posibble to this email id(firstname.lastname@example.org) or call me to this no(9393575330