Question about Ruud Central System Air Conditioner
When thermostat is shut off, squirrell cage fan keeps running. faulty thermostat or motor? thank you. RT
Ensure you don't have a short in your therm wires. Disconnect them, if the furnace continues to run, you have a lockout problem at your furnace. When the motor on the fan fails, it wont run. Check for led codes on the control board. If you don't have led codes, turn off the power to the furnace at the breaker, and watch the unit. If nothing happens, connect the thermostat. If nothing happens still call for heat. Let the therm run through it's cycle, and if the bower runs continuous again, let me know we can walk through that situation.
Posted on Dec 05, 2008
Probably the fan switch stuck on the fan combination control or improperly adjusted. Turn power off, remove red wire on the relay from the fan motor. Isolate so no short will happen and turn power on.The motor should not run. The fan relay could stick also. You will have to use a volt meter and see if there is voltage on the coil terminals on the fan relay. Put 1 lead to ground and touch only the terminal for the coil on the relay with the other meter lead.It should not have 120volts. If it does it is not the fan relay but possibly a limit sending power to the relay. Try that first thank you J
Posted on Dec 19, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 05, 2014 | Heating & Cooling
Apr 24, 2012 | Mastercool 67471 Evaporative Cooler Air...
Sep 24, 2011 | Ruud UBHC Air Conditioner
Jul 07, 2009 | Heating & Cooling
Mar 19, 2009 | Goodman CLQ36AR49 Air Conditioner
Jan 03, 2009 | Goodman CLQ36AR49 Air Conditioner
Jun 20, 2008 | Friedrich Heating & Cooling
469 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: