Question about True GDM-12 Refrigerator Commercial
Our TRUE GDM soda machine (glass doors) for commercial use.. is not making the soda's cold... I called someone in and hes charging $95 just to come out and look at it tom.. meanwhile i put the sodas in the back cooler for customers.. Any suggestions as what could be the problem... yesterday my brother was restocking all the sodas and had the glass doors opened for 2 hours.. and later at night we noticed that it wasnt cooling the sodas.. I changed the temp about 3-4 times but its not making any difference and only warm air is being blown out of the fans.. not cold air... and when u slide the doors open it stink..PLEASE HELPPP!!!... I dont have much money to pay someone to fix it.... ANY SUGGESTIONS???
If the cooler has power, the condesor fan (bottom) and evaporator fan (top) are spinning put your hand on the compressor. Do you feel a vibration? if so, you probably have a refrigerant leak. If not (if its clicking or nothing at all) its a compressor issue.
Posted on Aug 13, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 16, 2014 | True GDM-12 Refrigerator Commercial
May 04, 2012 | True 49 cu. ft. / 1388 liter Commercial...
Jul 02, 2009 | True GDM-12 Refrigerator Commercial
Jun 08, 2009 | True GDM-12 Refrigerator Commercial
Apr 14, 2008 | True 49 cu. ft. / 1388 liter Commercial...
411 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: