Question about Heating & Cooling
Did they indicate on a paper what they are getting for pressure under full-load? You should be getting between 9.5 and 10.5 inches of water column when all appliances are running. An orange flame indicates low gas pressure, not enough air mixture, or dirty burners. The intermittent condition when cooler outside makes me think that you have a bad propane regulator or too high of moisture in your propane tank. Did you change companies for price or quality of service? You may have made a bad choice.
Posted on Dec 05, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 14, 2015 | Eaton Nc-1425-5a Gas Valve
Jun 06, 2014 | Heating & Cooling
May 24, 2014 | American Range AF45LP Deep Fryer
Nov 02, 2012 | Blue Flame Heating & Cooling
Feb 01, 2011 | Reddy Heater RLP100 Portable Forced Air...
Oct 08, 2009 | Weber Gas Go-Anywhere Grill
Feb 10, 2009 | GE Profile Spectra JGBP90 Gas Kitchen...
Oct 26, 2007 | Reddy Heater-30,000 BTU Propane Forced-Air...
Oct 12, 2007 | Reddy Heater-30,000 BTU Propane Forced-Air...
Apr 24, 2017 | Heating & Cooling
97 people viewed this question
Usually answered in minutes!