Question about Air Conditioners
Did they indicate on a paper what they are getting for pressure under full-load? You should be getting between 9.5 and 10.5 inches of water column when all appliances are running. An orange flame indicates low gas pressure, not enough air mixture, or dirty burners. The intermittent condition when cooler outside makes me think that you have a bad propane regulator or too high of moisture in your propane tank. Did you change companies for price or quality of service? You may have made a bad choice.
Posted on Dec 05, 2008
Tips for a great answer:
Mar 10, 2011 | Air Conditioners
Feb 28, 2011 | Air Conditioners
Dec 12, 2010 | Air Conditioners
Dec 02, 2010 | Air Conditioners
Jan 10, 2010 | Air Conditioners
Aug 19, 2009 | Intertherm P3RA-048K Air Conditioner
Jan 05, 2009 | Air Conditioners
Jan 03, 2009 | Air Conditioners
Nov 29, 2008 | Air Conditioners
97 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: