Question about Heating & Cooling
Look for limit switches, you can find one or two manual push button switches near the exchangers. If that doesn't work, find the primary limit switch it is on the wall of the exchangers and does not have a manual botton to reset, get a paper clip and bypass those two wires, turn power back on then see if it works... Try the same thing with the manual limits, they have one wire coming in one going out, if continuity is broken furnace will not start. You must not leave the paper clip in, take the bad limit and replace it..
Posted on Dec 04, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 02, 2017 | Gibson Heating & Cooling
Feb 16, 2015 | Gibson KG7TC060D24B 60,000 BTU 95.1% Gas...
Feb 10, 2015 | Heating & Cooling
Feb 13, 2014 | Gibson Gas Furnace 60000 Btu 90% Afue...
Look on the back of the bottom cover... it should tell you what the blinking means...
Here is a tip that will help you try to figure out why your furnace is not working.
Basic Furnace or Heating System Troubleshooting
Feb 03, 2011 | Gibson Heating & Cooling
Oct 20, 2010 | Heating & Cooling
Nov 08, 2009 | Heating & Cooling
Feb 06, 2009 | Coleman Propane Forced Air Heater...
Jan 17, 2009 | Honeywell Electronic Programmable...
Jan 16, 2009 | Heating & Cooling
259 people viewed this question
Usually answered in minutes!