Question about Air Conditioners
Look for limit switches, you can find one or two manual push button switches near the exchangers. If that doesn't work, find the primary limit switch it is on the wall of the exchangers and does not have a manual botton to reset, get a paper clip and bypass those two wires, turn power back on then see if it works... Try the same thing with the manual limits, they have one wire coming in one going out, if continuity is broken furnace will not start. You must not leave the paper clip in, take the bad limit and replace it..
Posted on Dec 04, 2008
Tips for a great answer:
Feb 13, 2014 | Gibson Gas Furnace 60000 Btu 90% Afue...
Oct 19, 2013 | Gibson Gas Furnace 60000 Btu 90% Afue...
Feb 16, 2011 | Air Conditioners
Look on the back of the bottom cover... it should tell you what the blinking means...
Here is a tip that will help you try to figure out why your furnace is not working.
Basic Furnace or Heating System Troubleshooting
Feb 03, 2011 | Gibson Air Conditioners
Dec 05, 2010 | Air Conditioners
Nov 20, 2010 | Air Conditioners
Oct 20, 2010 | Air Conditioners
Nov 21, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jan 16, 2009 | Air Conditioners
Jan 06, 2009 | Air Conditioners
Dec 05, 2016 | Air Conditioners
246 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: